For sprinkler system pipe routing through walls and beams, make sure the appropriate sleeves are provided as per approval shop drawings and specification during the construction of structural elements. Fittings for the changes of direction or elevation shall be selected and installed as per the specification and approved shop drawings. Transfer the pipes from the stores to the areas which …Read More »
Download Method Statement For Installation, Testing & Commissioning Of Wet Chemical Fire Suppression System For Kitchen Hoods
Method Statement For Installation, Testing & Commissioning Of Wet Chemical Fire Suppression System For Kitchen Hoods Download Package Contains the Method Statement + Checklist for Installation + Checklist for Testing & Commissioning + Inspection & Testing Plan + Risk Assessment You only need to change project name and insert logos etc and the same shall be ready to be submitted for approval from …Read More »
Download Method Statement for Installation, Testing and Commissioning for the Clean Agent System Download package contains the Method Statement + Checklists for Installation, testing, pre-commissioning & commissioning + Inspection & Testing Plan + Risk Assessment. You only need to change project name and insert logos etc and the same shall be ready to be submitted for approval from consultant/clients. Below is …Read More »
Operating Instructions sprinkler system, landing valves, hydrant valve, hose reel valve, and extinguishers.
Operating Instructions for fire fighting system including sprinkler system, landing valves, hydrant valve, hose reel valve, and extinguishers. I. SPRINKLER SYSTEM Alarm Valve (i) Setting up of an Installation Control Valve assembly. State of Plant: Fire protection system mains pipework charged to system pressure up to the upstream side of Installation Control Valve. All Normally Closed (NC) Valves on trim …Read More »
Instruments & Tools Required for Testing & Commissioning Of Firefighting Sprinkler System Valve operating keys. Calibrated Pressure Gauges Heat gun Torque tester Flexible Hose Drums 300 liter to 500 liter Testing & Commissioning Sequence Pre-Commissioning Phase Below are sprinklers System Pre-Commissioning Checks: Before commissioning the system the following shall be ensured. a) The Installation and pressure testing of the pipes …Read More »
The objective of this document is to ensure that the room integrity tests in the 200 Bar gas fire extinguishing protected rooms are carried out correctly. The room integrity test will ascertain, whether the room will retain the design concentration of the FM 200 or Inert suppression gas for a period of 10 minutes. EQUIPMENT LIST Canvas Sheet Air Current …Read More »